The Occupational Safety and Health Administration (OSHA) and the National Electrical Code (NEC), require that electrical panels have a minimum of 3 feet (36 inches) of clearance and a minimum headroom of 6.5 feet or the height of the equipment whichever is greater.
How much space is needed around an electrical panel?
The space around electrical equipment should always be clear to be on the safe side. There should be at least 3 feet of space in front of equipment with a 30 inch width as well as 612 feet of headroom space.
Can you put something in front of electrical panel?
Just don’t put anything heavy or unwieldy in front of the panel, Mr. Wismer added. Or “you’ll have to get those Magic Sliders they show on TV for sliding the furniture around.”
What is the code for electrical panels?
Breaker panel must be at least 4 feet off the ground, but no higher than 6 feet. The panel door must be able to open at least 90 degrees. Working space around the breaker panel must be at least 30 inches wide and 72 inches from the ground up.
What is the minimum width of the working space required at an electrical panel that is 24 wide?
wide that contains over current devices, switching devices, or control devices, there shall be one entrance to an egress from the required working space not less than 610mm (24 in.) wide and 2.0m (6½ ft.) high at each end of the working space.
How far does an electrical panel have to be away from a window?
You are required to maintain a 3′ clearance away from the drip loop of the riser on the service where the utility company squeezes on there wires. This 3′ clearance must be maintained from the sides and bottoms of any window or door that opens, and also the 3′ is required away from any deck, stoop, porch or the like.
Can I cover my electrical panel with a picture?
For a quick fix, try hanging a painting or covered frame over it. A circuit breaker can also be hidden inside a cabinet as long as you keep it accessible. If you like painting, try using spray paint to blend the box in with the rest of the room.
Can a electrical panel be in a bedroom?
NEC does allow for electrical panel installation inside a bedroom. Bedrooms meet the NEC workspace requirements for electric panel installation. You can find electric panels inside bedrooms in condos or small houses where space may otherwise be limited.
Can an electrical panel be over a countertop?
You cannot put it over anything. You cannot put it next to anything. There must a clear space in front of the panel for an electrician to stand. … In your case, locating the panel under a counter would require an electrician to work on his or her knees when working in the panel.
What is the standard height of panel board?
The actual panelboard height is 5 feet, 4 inches, but it is mounted 20 inches from the floor. The top of the panelboard is 84 inches (7 feet) above the floor. In this installation, no circuit breaker (in its highest position) is more than 6 feet, 7 inches above the floor.
What is the minimum height for a breaker box?
Height. The minimum height for a circuit breaker box is 4 feet, though the ideal height is between 5 feet and 6 feet. The maximum height allowed for the circuit breaker box is 6 feet.
What is minimum electrical clearance?
110-26 of the National Electrical Code (NEC): 1) at least a 3-ft clearance in front of all electrical equipment; 2) a 30 in. -wide working space in front of equipment operating at 600V or less; and 3) minimum headroom clearance of 6 ft or the height of the equipment, whichever is greater.
What is the minimum clear working space in front of electrical equipment?
To be on the safe side, the working space and space around electrical equipment should always be clear per 110.26(A), if possible. As a basic rule, there should be at least 3 feet of space in front of all equipment with a 30 inch width as well as 6½ feet of headroom space.
What is the minimum required height of the working space?
Like the dimension for width of working space, there is a minimum dimension for working space height. If the height of the electrical equipment is 61/2 feet or less, the minimum height shall be 61/2 feet. For example, the height of a panelboard installed on a concrete block wall is 5 feet, 10 inches.