Does an electrical panel have to be on an outside wall?
3 Answers. They are almost always on an exterior wall. In some areas they are on the outside of the exterior wall – outside your house. Most inspectors would tell you that a garage (interior or exterior wall) or in the basement exterior (right where the line comes in) are the two best locations.
Where can you not have an electrical panel?
What electrical panel locations are prohibited?
- Where exposed to physical damage.
- In the vicinity of easily ignitable material. Clothes closets are specifically noted as an area with easily ignitable material (hanging clothes).
- In bathrooms.
- Over steps.
What is the code for electrical panels?
Breaker panel must be at least 4 feet off the ground, but no higher than 6 feet. The panel door must be able to open at least 90 degrees. Working space around the breaker panel must be at least 30 inches wide and 72 inches from the ground up.
How much clearance is needed around an electrical panel?
The Occupational Safety and Health Administration (OSHA) and the National Electrical Code (NEC), require that electrical panels have a minimum of 3 feet (36 inches) of clearance and a minimum headroom of 6.5 feet or the height of the equipment whichever is greater.
How far does an electrical panel have to be from a window?
As far as between the window and the door, as long as the working clearances will be complied with, and you are not installing the panel in a bathroom, you should be alright doing it. (working clearance is 36″ deep – or in front of the panel- and at least 30″ wide, also in front of, up to a height of 6’6″, minimum.
Can I build a closet around my electrical panel?
ANSWER: According to Section 240-24(d) of the National Electrical Code (NEC), which says “Overcurrent devices shall not be located in the vicinity of easily ignitable material, such as in clothes closets,” you are not permitted to do this.
Can a electrical panel be in a bedroom?
NEC does allow for electrical panel installation inside a bedroom. Bedrooms meet the NEC workspace requirements for electric panel installation. You can find electric panels inside bedrooms in condos or small houses where space may otherwise be limited.
What is the most common location for electrical panels in a house?
The main service panel is typically located in the basement, or (in a house without a basement) in a utility room. Some homes will also have a sub-panel, which is a smaller version of the main panel, to control electrical circuits in a garage, a workshop, or other outbuilding.
How high can I mount my electrical panel?
A height limit applies to mounting a panel box. The circuit breaker at the top of the box may not be higher than 6-foot 7-inches from the floor. A permanent platform must be below the panel box if the top circuit breaker exceeds this specific height. No defining height is mandated from floor to panel box base.
What is the minimum height for a electrical panel?
Height. The minimum height for an electrical box is 4 feet, although the ideal height is between 5 feet and 6 feet. The maximum switch height is 6 feet.
Is it legal to cover an electrical panel?
Is It Legal To Cover An Electrical Panel? You are allowed to cover your electrical panel but it must be easy to open, can not interfere with the opening of the steel door of the panel and you have to make sure you have full access to all of the breakers.
How far does electrical panel have to be from plumbing?
3 of the IRC specifies that a a dedicated space must exist around the panel and must be kept free of pipes, ducts and any equipment not pertinent to the electrical installation. This space extends from the floor to the ceiling or to a point 6 feet above the top of the panel, whichever is lower.